Cooling Energy Ultrasonic Flow Meter – EUF1568L
Hurricane EUF1568L series flow meter is designed to measure the cooling energy, hot energy continuously. With the advanced digital technology and intelligent self-adjust sound technology, the flow meter with features of high reliable and low maintenance cost.
With 2 temperature sensor inputting, build-in heating/cooling energy calculator, it makes the EUF1568L calculate the value of energy easily.
The EUF1568L is suit for the measurements on concentration supply of cooling, heating energy; for buildings, stores and residential etc. The sensor can choose from clip-on type, plug-in, the tube-stages etc three installation way, according to the real application.
EUF1568L is an Ultrasonic flowmeter which with advanced modular unibody design, independent menu operation, LCD backlit, product transmitter protection level IP65, sensor protection level is IP68, can be used in damp, such as for the use of harsh environment.
Can be used in various application with RS-485 communication interface, 4-20 mA current signal, Modbus, support product all-weather working.
Standard Configuration of EUF1568L
1. Flow Transmitter
2. Flow Sensor
3. Pipe tie
6. Temperature Sensor
- Measure heat energy and cooling energy separately.
- Measurement accuracy can reach 1.0%.
- 50,000 hours no-failure operation testing.
- Lifetime of press key is above 200,000 times.
- High precision matching temperature sensor.
- The sensor can choose from clip-on type, plug-in, the tube-stages.
- RS-485 interface, Modbus protocol.
- Carbon steel
- Stainless steel
- Central Air Conditioning in Buildings
- Cooling Energy or Heating Energy measurement
Suitable for water, liquid without mass of impurities, particle, suspended or bubble, and fluid full of pipe
Connection mode & Dimensions
⇒ Connection diagram
⇒ Outer dimension of EUF1568L transmitter
The size of sensor
Size of Anti-explosion casing
Installation, choose points
It is very easy to install the ultrasonic flow meter. Choose one suitable checking point, set the pipe parameter on the flow meter, and fix the transducer on the pipe, and then the flowmeter works. Please take reference on the rules as below while installing.
The installation of ultrasonic flow meter is the most simple and quick in all flow meter. Only choose one suitable checking point, input the pipe parameter to the flow meter and fix the transducer on the pipe then can make the measurement. Please take reference on the rules as below while installing.
Checking-point select principles
1.Get avoid from the position point 6 and 12 at o ‘clock direction to avoid signal attenuation due to the sediment at the bottom of the pipe or the bubble and cavitations.
2.Adequate consider the deposit condition within the pipe, try to choose the part without deposit for measurement. When completely meet the conditions, it need to take deposit into consideration as lining for better measurement accuracy.